Paging systems continue to be very effective notification tools today. Moreover, technology has progressed the paging system beyond the traditional loud speaker where now sophisticated systems can be zoned and addressed to as-needed areas through a plethora of different communication devices.
However, there is a clear distinction between a good paging system and a mass notification system.
Mass Notification and Emergency Communication, or MNEC, systems have very specific requirements.
In comparing an MNEC system with a paging system the most notable distinction is a mass notification system must meet the STIPA requirement for intelligibility.
STIPA, or the Sound Transmission Index for Public Address, is an industry standard that tests for the clarity of a message received.
As long as a reading of 0.5 or greater is met on the STIPA scale, the designed environment meets the requirement for mass notification.
Alongside the STIPA requirement, the National Fire Protection Agency (NFPA), also calls out in code #72 that a mass notification system must produce a noise level that is 10 decibels greater than the ambient background sound in private spaces and 15 decibels in public spaces.
The NFPA is stipulating that the noise source for an audible message in a mass notification system must be 10 – 15 dB above that ambient background sound, because in their estimation, the difference in noise to background sound is distinct and produces an intelligible instruction at that level.
Furthermore, as part of an overall design in a MNEC system, Acoustically Distinguishable Spaces (ADS) must also be identified. An ADS is nothing more than articulating the differences between spaces for use and noise control.
Lencore’s n.FORM™ Solution meets the design intent for a Mass Notification Emergency Communication System. The difference lies in the need for merely delivering an audible signal that may or may not be an effective means of communication and a mass notification system that is clearly defined with intelligibility in mind.